The cable are mainly used for power distribution in power stations, industrial installation and switchgears, as well as in local mains. Able to bear certain traction during installation. For fixed installation underground, in interior premises, cable ducts, in the open air and in water if no risk of any mechanical damage is to be expected. Laying single core cable in magnetic ducts is not allowed.
Rated voltage: / 1 kV
Maximum Conductor Temperature: under normal (90℃), emergency (130℃) or short circuit no more than 5s (250℃) conditions.
Min. Ambient Temp. 0℃, after installation and only when cable is in a fixed position
Min. Bending Radius: 20 x cable for single core
15 x cable for multi core
International: IEC 60502, IEC 60228
China: GB/T 12706
Other standards such as BS, DIN and ICEA upon request
CE, RoHS, CCC and more others at request
More information please click here.